A slight lead exceedance in a standing sample of water at the school. We are taking corrective actions to ensure the issue is resolved by the requirements of the Regulation and/or as directed by the Medical Officer of Health.
Herman APPENDIX A Letter (May 22 2018).pdf
Herman APPENDIX B Letter (May 22 2018).pdf
The custodian will now flush the building's plumbing on a daily basis. The sample results indicate the flushing ensures that lead levels remain below the limit and no further action is required.
For further questions, please contact the school.